Great Australian beer thanks to German technology
XXXX – a real brand
Situated in Milton, a suburb of Brisbane at Australia’s east coast, the Castlemaine Perkins Brewery produces one of the country’s most famous beers called XXXX ( www.xxxx.com.au ). The brewery belongs to the Lion Group, one of the leading beverage and food companies of Australia and New Zealand. But – no water, no beer!
The brewery already used a chlorine dioxide plant Bello Zon® CDVb for one reverse osmosis (RO) water main providing water for CIP applications, tunnel pasteurisers and wash-down water. In 2014, the company decided that one brewhouse water main for brewhouse processes and one deaerated liquid (DAL) water main for after-brewing processes should also be treated with chlorine dioxide due to the previous positive experience. So, the challenge was to use one single unit for generating the required high amount of ClO2 for the treatment of three different water mains.
- Disinfection of utility water using chlorine dioxide plant with capacity of 300 m3/h
- ClO2 concentration of max. 0.8 ppm and total ClO2 generation of 240 g/h
- One single unit used for three different water mains
Bello Zon® CDVc – the all-in-one solution
ProMinent Australia supplied a turnkey solution to the Castlemaine Perkins Brewery, which was installed and integrated into the customer’s SCADA system by contractors. However,
commissioning and an inspection test plan was again carried out by ProMinent experts.
The scope of supply comprised a modified Bello Zon® CDVc (240 g/h) plant, a ClO2 storage module and three dosing pumps Sigma 2 Control b to service two post-carbon filter mains and the existing utility water main. As well, transfer of ClO2 dosing to the utility water main from the existing ClO2 system to the new system was provided.
The disinfection system is designed to produce a ClO2 stock solution between 500-1,000 ppm, which is achieved by dosing 9% acid and 7.5% chlorite proportionally to the make-up water flow. This stock solution is then used for the treatment of brewhouse, DAL and RO water flows. The control of the three ClO2 dosing pumps can be increased or decreased via a “dosing ratio“ in the SCADA system.
Disinfection – efficient and reliable
The Lion Group with its famous brands relies on successful operation of chlorine dioxide systems not only at the Castlemaine Perkins Brewery in Milton, but also at the SA Brewing and the Toohey’s sites. All installations were executed without bigger problems and since start-up, operations are running smoothly. The Bello Zon® CDVc system does what it should do: providing disinfected water in the required quality to the three water mains – constantly and safely. Well, then: Cheers!